Model NO.: MS
Impeller Number: Single Stage Pump
Influent Type of Impeller: Double-Suction Pump
Pump Casing Combined: Horizontal Split Pumps
Material: Ss.Bronze, Cast Iron
Application: Water, Fire, Farm Irrigation, Building
Transport Package: Wooden Case
Driving Type: Motor or Engine
Working Pressure: High Pressure Pump
Position of Pump Shaft: Horizontal Pump
Mounting Height: Suction Centrifugal
Usage: Circulating Pump
Specification: CE, ISO, SGS
Double Suction Split Casing Pump
Overview of Double Suction Split Casing Pump
Model MS Horizontal split case Fire pump is a single-stage double-suction horizontal split centrifugal pump and used to transport pure water and the liquid of both physical and chemical nature similar to those of water, the maximum temperature of which must not be over 80oC , suitable for water supply and drainage in factories, mines, cities and electric stations, waterlogged land drainage and irrigation of farming land and carious hydraulic projects.
Application for Double Suction Split Casing Pump
Aerospace Oil & Gas
Building industry Power Station
General Industry Pharmaceutical
Marine Pulp & Paper
Mining & Aggregate Water & Waste water
|General water supply||Circulation of HVAC building systems, water booster service, boiler feed, general circulation service and more.|
|Agriculture / Food / Beverage||Irrigation, water supply, food processing beverage processing, fertilizers.|
|Manufacturing||Pulp and paper fans, plastic & rubber, metal & steel, pharmaceutical, paper mills, air wash, marine ballast service.|
|Fire / Disaster Relief||Fire pumps, fire protection, flood control, disaster relief, federal / military.|
|Utilities : Water / Wastewater||Power Generation stations, dewatering, desalination, energy recovery turbines|
|Chemical / Mining||Chemical plants, refineries, petroleum distribution, coal sites, ethylene glycol pumping.|
|1.Casing for Centrifugal horizontal Large flow pump farming irrigation equipment |
The volute casing is split on the horizontal centerline with the suction and discharge nozzle cast integral with the pump casing. The upper casing is accurately located on the lower half by the use of dowel pins. The upper casing can be removed to inspect the interior of the pump without disturbing the pipe connections or pump alignment. The suction and discharge flanges contain tapped holes for vacuum and pressure gauge. At the bottom of the flanges, there are tapped plugs for water drainage.
The impeller is static-balance calibrated, fixed with the muff and the muff nuts in both sides and its axial position can be adjusted via the nuts and axial force gets balanced by means of the symmetrical arrangement of its blades, there may be residual axial force which is borne by the bearing at the axle end.
The pump shaft is supported by two single-column centripetal ball bearings, which are mounted inside of the bearing body on both ends of the pump and lubricated with grease. The dual-suction seal ring is used to reduce the leak at the impeller
|4. Seal Type|
There is gland seal type and mechanical seal type.
Double Suction Split Casing Pump types
Fire pumps are usually used for supply water as the fire fighting systems booster, and then ensure the continuously water supply. If on fire, can extinguishment in a quick way.
The fire pumps can have below types:
It have fire fighting truck pump, marine fire fighting pump, construction fire fighting pump, and some other fire pumps. Different projects, will have different names, but the function is same. However the pump construction will have little different. We can choose the better solutions for different projects.
It will have water supply fire fighting pump, and booster fire pump.
S Series Centrifugal Double Suction Horizontal Split Case Pump power loss
There only a part of the mechanical power of the centrifugal pump getting from the driver equipment, convert to the centrifugal power and then delivered to the liquid power. The another part was loss. The reasons are below:
1. Hydraulic loss: Created for the liquid impact, vortex and friction in the pump. The impact and vortex hydraulic loss is because of the the liquid change the flow direction. Besides, when the liquid flow, it will have friction when meet the pump passageway.This kind of loss depend on the length, volume, shape, and surface roughness of the passageway and the liquid flow speed and other character.
2. Volume loss: It resulted for the powered liquid will channeling are leakage. The general pump volume efficiency is 0.93~0.98%. Improve the seal ring and shaft seal construction, can reduce the volume loss and increase the volume efficiency.
3. Mechanical loss: It is caused by the friction of liquid and impeller plate surface, also named dick friction loss of impeller, and the pump shaft friction when rotated in the packing, bearing, balancing parts and other mechanical parts.